Solar panel fires
The cost of powering homes, farms and businesses has increased exponentially during the past 30 years. To combat the uncertainty, or in many cases to create a more “green” environment, residents and business owners have turned to solar as an alternative energy source. According to Brendan Dunn of Deep Blue Training Associates, since early 2000 the production of photovoltaics doubled every two years until 2008, when it doubled in just one year.
One aspect of PV systems that is not often considered is the safety factor, most notably the risk of fire. While not necessarily a greater risk than other energy arrangements, photovoltaic systems do require special consideration by fire departments and first responders in the instance of an unexpected combustion.
Dunn noted that electrical shock presents the paramount hazard when dealing with solar power. More importantly, Dunn pointed out, “power from the grid can be controlled and de-energized. Power from distributed power generation (solar) present serious challenges for emergency responders.”
“A photovoltaic system generates electricity when the sun is shining, when it is receiving sunlight,” he continued, “thus a photovoltaic system can never be shut off (during daylight hours).”
It has been proven that artificial illumination and extensive fire can provide enough illumination to generate electricity in a PV module, although low ambient light, such as full moonlight, cannot. Dunn pointed out that firefighters must realize that when a PV module is damaged overnight, as soon as the sun rises electrical generation will once again start.
Additionally, lightning may cause a power surge during nighttime operations when the system would be normally off. If electrical storms are occurring during firefighting operations at night, PV modules should be treated as though they are energized.
“Emergency responders must always treat solar powered systems as energized,” he warned. “They must also realize that during a fire these units may become damaged, exposing them to live electrical conductors.
“Although solar power systems will have disconnects, these disconnects will only isolate power and will keep power from the building circuitry. The amount of energy is dependent on the size of the system; a large commercial system generates much more energy than your typical residential system. More modules equals more energy.”
Any size solar power system can produce enough energy to be lethal. To minimize or eliminate the electrical output from PV solar modules, departments should cover the module with a 100 percent light-blocking tarp.
Dunn also recommends that emergency personnel wear a self-contained breathing apparatus since the smoke generated by burning materials used to construct the PV modules may be toxic. He also suggests that the handling of materials from PV modules should be done with full protective clothing on, as they present a dermal exposure.
Naturally, the best way to combat the problem of fire in photovoltaic systems is to never have the fire begin in the first place. While the cause of some fires is unavoidable, such as those resulting natural occurrences or unforeseen circumstances, residents can take steps to minimize the risks.
Most modern PV systems do not use batteries. Encouraging the selection of battery-free systems greatly reduces the risk of self-combustion fires. This setup, however, requires remaining on an electrical “grid,” which sometimes is not an option in rural settings. Physically, battery-free systems produce electricity for use on site or for transmission to the local utility.
Proper installation of roof-mounted PV systems is tantamount to safety. In his 2010 article, “Fires Caused by Solar PV Systems: Reducing the Risk,” IDC Energy Industry Insights Community Research Manager Jay Holman noted that “improper installation is consistently identified as one of the greatest risk factors related to arc-faults, so ensuring installers are well qualified and having the installation inspected once it is completed are the two steps that are likely to have the greatest impact on arc-fault risk.”
The 2011 National Electric Code required inclusion of arc-fault protection in rooftop solar PV systems. For owners of PV systems that were installed prior to the 2011, retrofitting for arc-fault protection is optional.
- Only hire licensed solar contractors. Look for solar installers who are certified by the North American Board of Certified Energy Practitioners.
- Only buy high-quality equipment. For minimal fire risk and optimal energy output, stick with panels that have been tested and approved by Underwriters Laboratories.
- Grounded vs. ungrounded DC systems: This is a bit technical, but if you have the choice between ground fault protection vs. ungrounded fault protection, choose the latter. New safety standards set forth by UL and the National Electrical Code are making ungrounded DC systems the standard.
- Use proper isolator switches. This is also a slightly technical point, but always make sure your system has the proper DC isolator switch between the inverter and panels.
- Upgrade your roof. This is a drastic measure, and usually unnecessary. But you can reduce potential blazes by using fire-resistant roofing materials like metal, composite or cement tiles instead of wood or tar alternatives.
Solar panel fires — No Comments
HTML tags allowed in your comment: <a href="" title=""> <abbr title=""> <acronym title=""> <b> <blockquote cite=""> <cite> <code> <del datetime=""> <em> <i> <q cite=""> <s> <strike> <strong>